Per unit system is a method
used in Electrical Engineering for the analysis to express the voltage,
current, kVA and impedance in per unit of base or reference values of these
quantity.

Per Unit values for any system
is obtained by choosing a set of some base or reference value which can be
chosen arbitrarily. But for the sake of calculation, it is common practice to
choose the Rated quantities to be the Base or Reference Value.

Per Unit or pu value is
defined as,

**Per Unit Value = Actual Value of Quantity / Base Value of the Quantity**

For illustrating the p.u
system, we take single phase two winding Transformer for example.

For High Voltage Side, first
of all we need to select base values for calculating the p.u value.

Let us assume, V

_{BH}= Base value of Voltage
And I

_{BH}= Base value of Current.
Therefore,

Base value of Impedance Z

_{BH}= Base Value of Voltage/Base Value of Current
= V

_{BH}xV_{BH}/V_{BH}xI_{BH}_{ }=

**(V**

_{BH})^{2}_{ }/

**Rated kVA**

_{ }

=

**(kV**_{BH})^{2}_{ }/**Rated MVA**_{ }
Hence,

p.u
value of r

_{eH}(Equivalent Resistance reffered to HV side) = Actual value of r_{eH}/ Z_{BH}_{}

Similarly
for LV side of Transformer,

If
we choose Rated LV voltage and Current as the Base value, then

Base value of Impedance Z

_{BL}= Base Value of Voltage/Base Value of Current
= V

_{BL}/I_{BL}_{}

= V

_{BL}xV_{BL}/V_{BL}xI_{BL}_{}

_{ }=

**(V**

_{BL})^{2}_{ }/

**Rated kVA**

_{ }

_{}

=

**(kV**_{BL})^{2}_{ }/**Rated MVA**_{ }
Now,

p.u
value of rated voltage on HV side = V

_{BH}/V_{BH}= 1
p.u
value of rated current on HV side = I

_{BH}/I_{BH}= 1**Thus we see that p.u value of rated quantities is 1 if we chose rated quantities as the base or reference value. It shall also be noted that p.u value is a dimensionless quantity.**

Another important feature of
per unit system is that, for Transformer, the p.u value in HV side becomes
equal to the p.u value in LV side.

**(How?)**

_{ }Let Z

_{eL}= Equivalent Impedance when referred to LV side

Z

_{eH }= Equivalent Impedance when referred to LV side
So,

p.u
Impedance referred to LV side = Z

_{eL}/Z_{BL}_{}

Now,

p.u
Impedance referred to HV side = ZeH/Z

_{BH}_{}

But,
Z

_{eH}= Z_{eL}(N_{H}/N_{L})^{2}^{}

Therefore,

p.u
Impedance referred to HV side = Z

_{eL}[(N_{H}/N_{L})^{2}] / Z_{BH}_{}

= Z

_{eL}/ [Z_{BH}/ (N_{L}/N_{H})^{2}]
= Z

_{eL}/ Z_{BL}_{}

Thus from the above it is
clear that, Transformer equivalent parameters in p.u system are equal in HV as
well as LV sides.

**Why do we use Per Unit System?**

There are several reasons
for using a Per Unit System. Some of them are mentioned below:

- Similar apparatus like generators, transformers, transmission lines etc. will have similar per unit impedances and losses expressed on their own rating, regardless of their absolute size. Because of this, per unit data can be checked rapidly for gross errors. A per unit value out of normal range is worth looking into for potential errors.

- Manufacturers usually specify the impedance of apparatus in per unit values.

- Use of the constant is reduced in three phase calculations.

- Per unit quantities are the same on either side of a transformer, independent of voltage level.

- By normalizing quantities to a common base, both hand and automatic calculations are simplified.

- It improves numerical stability of automatic calculation methods.

- Per unit data representation yields important information about relative magnitudes.

## No comments:

Post a Comment